See what makes JMS Services the best choice for Alvordton OH!
It’s important to have a reliable plumbing, heating and air conditioner service that you can count on. That’s why since 1985, JMS Services has been the number one choice for the people of Alvordton, OH. Their operating philosophy is simple – they do things the right way, not the easy way. They guarantee their work and make sure it’s done right the first time, every time. Services include HVAC repair and maintenance, drain cleaning, sewer services and water heater installation. For professional, courteous and capable service, JMS Services is the only call you need to make.
Want to know more about the excellent service we offer? Read below to see what your neighbors in Alvordton, OH have to say about our work – then when you need plumbing and HVAC services you can count on, give us a call!
for Alvordton, OH
Our Reviews by City
Removed chunk of wax from sink drain and verified proper operation.
Customer already replaced the breaker himself Geo was running when I got here I installed a new condensate pump and checked the split on the water and was getting a 7° rise. However we need to schedule a tuneup ASAP to check the geothermal and to juice up the system.
Found breaker to be bad, quoted condo pump and new breaker. Customer approved repairs need to return asap to repair.
Found breaker was bad. Replaced with double pole 30 amp breaker. Verified amp draw and water heater is now working. No after hours fee charged due to installing unit earlier today.
Found that the capacitor had failed and the compressor nor the pumps were running. Capacitor was changed and ensured system was operating prior to leaving. System is a little low on water and Freon should be checked due to temperature rise in water. A tune up was recommended to go through system for general maintenance.
Install 50 Gallon Electric Water Heater
Installing a 4" clean out set to clear blockage. we will dig up a section of the yard, install clean outs and back fill. this does not include reseeding or hauling away excess dirt. Ran the camera and verified the house is draining We did hit the propane line, repaired the damaged section, insured no leaks and appliances are working Customer to call in the spring to cut the cleanouts closer to the ground as needed once the ground settles
Found the house backing up, water is leaking from fittings under the house No cleanouts Pulled the toilet and ran the medium machine, machine cannot make the turn and tries to go up the second toilet Tried pulling the other toilet and running from there, does the same thing Gave to owner options to add cleanouts or to add a pipe under the house for access Owner chose to add cleanouts Office to reschedule
Relit the pilot assembly Checked the capacitor for the blower motor Made sure the furnace is working before leaving Highly recommended carbon monoxide detectors due to the age
Installed new capacitor