See what makes JMS Services the best choice for Camden MI!
When it comes to plumbing, heating and air conditioner service, no one does it better than JMS Services. They’ve been the number one choice for the people of Camden, MI since 1985, and there’s a good reason why. Their services include HVAC repair and maintenance, drain cleaning, sewer services and water heater installation. They’re always professional and courteous, and they guarantee their work. They make sure it’s done right the first time, every time. So if you’re looking for the best in plumbing, heating and air conditioner service, give JMS Services a call. You won’t be disappointed.
Want to know more about the excellent service we offer? Read below to see what your neighbors in Camden, MI have to say about our work – then when you need plumbing and HVAC services you can count on, give us a call!
for Camden, MI
Our Reviews by City
Grace - Camden, MI 49232
Not the best service. Tech didn’t have the equipment with him, had to make another appointment. Tech was nice but not very knowledgeable. Not my best experience with JMS.
Tim - Camden, MI 49232
Very happy with the service. Christopher was very pleasant and professional.
Response from JMS Services:
We are incredibly grateful that you took the time out to leave us a 5-Star review.
Great Job Aaron!
Rich - Camden, MI 49232
Aaron was very professional. He has very good communication skills, a friendly disposition, along with great experience and skills!
Gave good advice!
James - Camden, MI 49232
Considerate but didn’t wear mask.
Larry - Camden, MI 49232
Installed new power vent water heater. Was not able to get old water heater out by myself so we will need to return to remove it.
When arriving at the customers house, I performed a leak check on their geothermal. I checked all the lines coming off the compressor. I found no leaks coming from there but when I started to check the coil, it started beeping 99%. I took it away put it on medium setting and it beat and I took it away again on low setting and it beat as well. I confirmed the unit not fit to be replaced. I gave a couple estimates to the customer.
A mouse has chewed through the wire for a second time I cut out that section of wire and resealed hole with a full tube of silicone. Condenser was completely plugged so I also clean that while I was here.
Performed AC tune up verified everything was working properly. Blower capacitor was changed. Recommend condenser capacitor replacement as terminals are rusty.
We will be extending the waterline to the new well tank that will be set by the well company when the new well is installed. Tied well tank to existing waterline and verified it was leak free as well as bled water off at kitchen sink.
Check system and found that thermostat wire was shorted out due to a rodent eating through the wires where it came to the wall. There’s not much slack there but I was able to isolate the two wires for cooling and electrical tape them so they would not short out anymore if anything else happens to these wires a new wire will have to be polled I was not able to access the thermostat wire from inside due to the ceiling being finished. I performed a quick check on the system and verified everything was operating properly however the unit does not have a filter in it it takes an 18 x 24 x 4 I let the customer know on the size and they are going to order. I also would recommend having a blower cleaning done due to it being dirty from not having a filter in there for a bit.
Checked the furnace Found the Ignitor bad Replaced the Ignitor Replaced the media filter at the owners expense Insured the furnace is working properly before leaving Furnace will need burners soon Owner will let us know if he wants to do them for next season
Found sump pump to be bad. Replaced sump pump and verified proper operation.
Installed new 50 gallon electric water heater verified there was no leaks
Found water heater to be issue. Quoted new water heater and customer approved.
Need to order a part
Performed regularly scheduled furnace maintenance to ensure system was ready to go for cold weather months. Cleaned the system, checked out all functionality, replaced filters. System looked good and is ready to go.
Installed gas line to heater in living room. Verified line was leak free and the lit pilot on heater in kitchen. Customer did not have the flex gasline needed to hook heater into new gasline. Customer is going to go to hardware and get his own flex line.
Replaced zone valve verified there was no leaks and that everything was working properly
Found no leaks from drain or water lines. Found evidence of water leaking behind the tub spout also found water from shower sprayer hits tub spout right where there is an opening going behind the wall. Siliconed the tub spout and informed customer to give that a try and if it is still leaking we will need to go through with a new shower valve and trim kit.
Repair water line that went to well pump
Found that wasps had built a nest in exhaust pipe cleaned out and verified operation also condo pump was not working cost wanted that replaced also customer sighed up for maintenance also
Found bad board on geo. Also found the drain for geo to be a bit plugged. Ran small machine through drain and we will need get back with customer on board.
Found capacitor to be bad. Replaced capacitor and verified proper operation
Customer had their sanitary line backing up. We ran large machine and camera down the line and got blockage open and verified that plumbing was operating properly.
Customer called and said that water was leaking under the kitchen sink. When I arrived on job site I did a thorough inspection under the sink and found that the supply line was leaking but due to the style of it everything under the sink needed to be cut out and rebuilt. I recommend replacing faucet and plumbing underneath the sink and customer approved. I then replace the faucet and stops and rebuilt stop going to dish washer. I then verified everything was leak free and cleaned up work area.
Perform Precision Tune Up on heat system and blower cleaning
Perform Precision Tune Up on heat system verified everything is operating properly
Perform Precision Tune Up on heat system and verified everything was operating properly