See what makes JMS Services the best choice for Napoleon OH!
It’s important to have a reliable plumbing, heating and air conditioner service that you can count on. That’s why since 1985, JMS Services has been the number one choice for the people of Napoleon, OH. Their operating philosophy is simple – they do things the right way, not the easy way. They guarantee their work and make sure it’s done right the first time, every time. Services include HVAC repair and maintenance, drain cleaning, sewer services and water heater installation. For professional, courteous and capable service, JMS Services is the only call you need to make.
Want to know more about the excellent service we offer? Read below to see what your neighbors in Napoleon, OH have to say about our work – then when you need plumbing and HVAC services you can count on, give us a call!
for Napoleon, OH
Our Reviews by City
The gas line has been checked around the water heater. I was not able to detect any leak in the gas line. I did notice when the water heater kicked on, I did smell propane, but then it went away. I had both bubbles and leak detector, and I still didn’t find any leaks or smell after it lit up. As of right now, the water heater is working in normal operation
Found broken waterline in crawlspace. Repaired waterline and found a broken chrome stop. Replaced chrome stop and verified proper operation.
Checked the furnace for the east side of home Found error code for loss of flame Checked and cleaned the flame sensor, 4.5 reading after cleaning, furnace was in the laundry room also can cause extra buildup on the sensor Checked the flue piping, b-vent needs to be insulated, temperature difference is causing condensation Owner will try to insulate himself Insured the furnace is currently working before leaving Made owner aware small chance the control board could be bad, I’m the same error code happens again he will need an estimate
Existing gas line to the garage tied into the house main and ran to new heater
Checked the furnace Found spider web in the gas valve Cleared the web out Insured the furnace is working before leaving
Found the water supply for the water heater leaking from the shark bite fitting Replaced the supply hose, insured no leaks New homeowner paying to transfer warranty Anna Cifranic Aacifranic@gmail.com 330-221-9271