See what makes JMS Services the best choice for Pioneer OH!
JMS Services is the only call you need to make when it comes to plumbing, heating and air conditioner service. They have been in business since 1985 and are the number one choice for the people of Pioneer, OH when it comes to these services. Their operating philosophy is simple – they do things the right way, not the easy way. This means that they guarantee their work and make sure it’s done right the first time, every time. For professional, courteous and capable service, JMS Services is the only call you need to make.
Want to know more about the excellent service we offer? Read below to see what your neighbors in Pioneer, OH have to say about our work – then when you need plumbing and HVAC services you can count on, give us a call!
for Pioneer, OH
Our Reviews by City
Barbra - Pioneer, OH 43554
Chris was thorough and professional.
Parker - Pioneer, OH 43554
Cummins - Pioneer, OH 43554
Great Service. Knowledgeable. Friendly.
Barbara - Pioneer, OH 43554
I would highly recommend JMS/Chris. They were here the next morning and he got my boiler furnace going, he explained what had happened and I need 2 parts that they will order. I also signed up for them to check it out on a yearly basis!! Trying not to be without heat again!!
Amanda - Pioneer, OH 43554
Did a wonderful job. Very nice ..
Response from JMS Services:
hanks for sharing your review with us and the community.
Derek - Pioneer, OH 43554
Response from JMS Services:
We are incredibly grateful that you took the time out to leave us a 5-Star review.
Walkup - Pioneer, OH 43554
Very professional service, polite and respectfull
Response from JMS Services:
Thank you for your feedback Tom. Our team is very thankful.
Alden - Pioneer, OH 43554
Ted - Pioneer, OH 43554
Very cordial . Good technician.
Judy - Pioneer, OH 43554
Tyler not pushy about my needing to update ac system. Will be in touch.
Sandra - Pioneer, OH 43554
Checked the sewer line The whole house is backing up, could not find a cleanout Pulled the toilet and ran the large machine through Cleared the blockage and verified with the camera Reset the toilet Cleaned up the workspace Insured no leaks and the house is draining properly Mail invoice
Installed new gas valve and verified proper operation.
Replaced the furnace trap due to it being plugged. Fired up the furnace Found problems with the heat exchanger, top of the furnace is burning hot, flame is abnormal, and soot build up in the exhaust, this most likely caused the trap to clog up Recommended replacing the furnace due to the issue Owner requested an estimate and will let us know Highly recommended carbon monoxide detectors due to the issue
Found trap to be plugged very badly. Attempted to clean it but it is very plugged. Need to give customer price and availability.
Installing a new ignitor to replace your current one that has failed and testing system for proper operation. Note: Replaced igniter found that burners would not ignite. Burner conditions are poor. Gas pressures were good. Unit is a garage heater that is connected to standing propane tanks with a rubber hose. Manually lit burners with lighter found the blower would not kick on. At one point the burner compartment area caught fire. Checked for vacuum on inducer motor which showed a reading of 1.1. Draft van was also not exhausting properly. Customer did not wish for me to continue a diagnosis. I terminated gas supply and shut gas valve off. Advised customer not to run furnace due to safety reasons as the heat exchanger exhibited signs of being clogged. Recommended replacing system. Photos/Videos have been uploaded and payment for igniter was collected.
Found igniter on furnace to be bad need to get a price and send customer an estimate on what it’s gonna cost to repair
Water line is froze or possible blockage in pipe from camp ground re doing plumbing at pump camp ground is going to take care of issue
Preformed a precision heating tune up everything is operating correctly
Preformed a precision heating tune up everything is operating correctly installed a new filter
Installed full valve for boiler. Found auto air vent in basement to be bad so recommended replacement to customer and customer approved. Verified everything was operating.
Found furnace had a dirty flame sensor cleaned flame sensor also found that there was a bunch of water leaking inside of furnace found that blower motor and inducer motor were both over amping informed customer of issue customer wanted a price on a whole new system sent customer a quote for a whole new system said he would let us know within a week special notes for install are in the form
Checked gas line from furnace to stove. Replaced flex line going to stove and installed a shut off. Verified no gas leak.
Inspected heat exchanger did not find any cracks heat exchanger is in good shape informed customer there was no cracks Also sent customer estimate for gold plan
Need to return to install an auto fill valve boiler is heating just not filling itself Tuesday works the best for the customer then after that any day except for before 230
Found intake to be clogged with snow took intake off top of furnace and shower customer how to put it back in when weather gets decent again
Installed new auto fill valve and new air separator verified there was no leaks
Added refrigerant to system and new locking caps Ran system to make sure proper system operation.
Replaced limit switch and verified operation of furnace
Found that auto fill valve on boiler was bad not allowing boiler to fill manually refilled boiler so that customer could have heat until we got a part also found that auto air vent on boiler is leaking customer wants to replace auto fill valve and auto air vents already accepted a quote for that
Found the kitchen sink backing up Ran the hand held machine down and cleared the blockage Put the sink back together and ran hot water down the line, insure no leaks and the sink did not back up Owner ran the dishwasher also and drain pump kicks on and was flowing Cleaned up work space
Checked the main sanitary line Line is backing up under the foundation Ran the medium machine through cleanouts in the basement Pulled out roots and debris Ran the machine a few more times and insured the line is clear, attempted to run the camera but it would not make the transition in the old cast pipe Recommended the owner start a root treatment Also found the main sewer with debris blocking the outlet in the man hole Recommended the owner call the city to have them come and clean out
This would be the most cost effective and safe option for this job.
Customer reported extraordinarily high humidity in their home. Checked their HVAC system, determined they weren't getting proper airflow when their AC unit was running due to some clogged filters. Replaced filters and corrected the issue.